After you have worked out the heat requirement for your room (AEL's easy-to-use BTU calculator will help you do this), how can you check that the radiator you have chosen will provide enough heat output?
There is a simple calculation to check if the radiator will provide sufficient heat output. You must check the “delta T”.
In the AEL radiator catalogue, a heat output figure is provided for each of the radiators, along with the radiator's dimensions. The heat output figure is reported for a specific "delta T". The delta T is the difference between a target room temperature and the average temperature of water in the radiator. The average temperature of the radiator depends on the temperature of the water entering and leaving the radiator, which may be different in your heating system.
delta T = (Room temperature) - (Average radiator water temperature)
If the delta T of your system is different from the one shown in the catalogue, then you will need to calculate a new heat output. This is easily done by multiplying the output figure in the catalogue by a correction factor.
Delta T (°C) | Correction factor |
5 | 0.050 |
10 | 0.123 |
15 | 0.209 |
20 | 0.304 |
25 | 0.406 |
30 | 0.515 |
35 | 0.629 |
40 | 0.748 |
45 | 0.872 |
50 | 1.000 |
55 | 1.132 |
60 | 1.267 |
65 | 1.406 |
70 | 1.549 |
75 | 1.694 |
The diagram below illustrates a case where the desired room temperature is 20°C and the average water temperature across the radiator is 70°C. The difference, the "Delta T", is 50°C.
If the “Delta T” in the catalogue is 50°C, it is perfect to just use the outputs shown in the catalogue (the correction factor for this system would be equal to 1).
For a system with “Delta T” other than 50°C, calculating the new output for the radiator is simple:
Radiator output in the AEL catalogue (based on delta T=50°C) = 194W
Your system's delta T = 35°C
From the table, correction factor = 0.629
Therefore, the output of your radiator = 194W * 0.629 = 122W
After you have worked out the heat requirement for your room (AEL's easy-to-use BTU calculator will help you do this), how can you check that the radiator you have chosen will provide enough heat output?
There is a simple calculation to check if the radiator will provide sufficient heat output. You must check the “delta T”.
In the AEL radiator catalogue, a heat output figure is provided for each of the radiators, along with the radiator's dimensions. The heat output figure is reported for a specific "delta T". The delta T is the difference between a target room temperature and the average temperature of water in the radiator. The average temperature of the radiator depends on the temperature of the water entering and leaving the radiator, which may be different in your heating system.
delta T = (Room temperature) - (Average radiator water temperature)
If the delta T of your system is different from the one shown in the catalogue, then you will need to calculate a new heat output. This is easily done by multiplying the output figure in the catalogue by a correction factor.
Delta T (°C) | Correction factor |
5 | 0.050 |
10 | 0.123 |
15 | 0.209 |
20 | 0.304 |
25 | 0.406 |
30 | 0.515 |
35 | 0.629 |
40 | 0.748 |
45 | 0.872 |
50 | 1.000 |
55 | 1.132 |
60 | 1.267 |
65 | 1.406 |
70 | 1.549 |
75 | 1.694 |
The diagram below illustrates a case where the desired room temperature is 20°C and the average water temperature across the radiator is 70°C. The difference, the "Delta T", is 50°C.
If the “Delta T” in the catalogue is 50°C, it is perfect to just use the outputs shown in the catalogue (the correction factor for this system would be equal to 1).
For a system with “Delta T” other than 50°C, calculating the new output for the radiator is simple:
Radiator output in the AEL catalogue (based on delta T=50°C) = 194W
Your system's delta T = 35°C
From the table, correction factor = 0.629
Therefore, the output of your radiator = 194W * 0.629 = 122W
BUILDING SERVICES helps designers, specifiers and buyers find the right companies and products to work with for all building services engineering projects. BUILDING SERVICES hosts the widest array of supplier details on the market, supported by case studies, articles and learning materials to help you identify the best solution for your project...Read more
Sign in or create an account to access all the info and tools on this website for free.